Leaking Floor Waste Drain and Pipe
A client from the North Rocks enquired about a leak that was concerning her. This leak was supposedly coming through the shower and down into her garage . Our professional team were abke to pressure test and dye test the area. Upon investigation, we figured out that the floor waste drain and pipe was leaking – we recommended to the client that these should be replaced.
How we helped
First of all, to begin fixing this issue we removed the old floor waste. The next step was to obtain any floor waste within a diameter of 100m and a spigot of 50mm. This would allow us to connect the new drainage, then we installed the new floor waste drain with a new seal and conducted a pressure test again. This had fixed the problem!
The client called the office to thank the staff that did the job, she claimed that we saved her money as she thought she had to replace her whole shower.