Blocked Sewer Line
Attempted to clear line with jet blast and we were able to clear to get in the sewer pipe inspection camera after inspecting and locating we found that the sewer lines had a collapsed shaft and also had several roots in different locations and dislodged pipe thru out line, we advised customer what should be done to completely fix the problem as the clients have had this issue for several years and advised that we need to replace piping
How we helped
We excavated down to the base of piping on the front of the property and removed all old defective piping. We then cleaned out the hole correctly and concreted the base of hole to support the new pipe. We connected onto Sydney water piping and raised up new upvc shaft and connected that onto the house line.
We raised inspection to floor level for future access. We filled the hole with blue metal and backfilled remaining hole with with soil. Finishing up, we compacted and cleaned up work area.
We also excavated house main sewer run from house to new shaft and replaced with new 100mm upvc and backfilled with blue metal and remaining soil.
After completion of works we put down the sewer camera to check our work and we can now say that out client will not have this problem again and would say their sewer is as good as new
Our clients were extremely happy with the result and clean-up of works as we took the time to cover the work area before starting
Thanks to the guys at fixed today your Sydney plumbing experts in drains